Purpose – wall hydrants box with the equipment mounted therein is intended for extinguishing with water from the water supply network of fires in buildings and objects in operation.
The cassette is mounted on the wall with dowels and consists of a body, a door with a handle, a drum on which a hose winding ending with storm couplings, a jet and a 2″ nozzle connected to the water supply network.
Materials – the cassette is made of steel (it can also be made of stainless steel). Aluminum cassette are also available.
Color – white, RAL red, powder coated.
Construction – The cassette is manufactured in accordance with BDS EN 671-2. Available as models KA-100 (ordinary) and KA-500 (luxury), with back and without back; cassette sizes w / h / d (mm) 600/600/180; a flat hose with a Ø 52 diameter and a length of 20 m.